Extra Thin Green LED Exit Sign - White Housing
Base Code: ELCLEDT-G
Compatible Battery: BAA-12
This item has been tested and meets safety standards imposed by the Underwriters Laboratories (UL).
This unit uses energy effecient and long lasting LED's.
This unit contains a battery for backup power. The battery must be connected during installation.
- UL 924, NEC and NFPA 101 Life Safety Code
- Listed for damp location
- ULTRA THIN injection-molded, VO flame retardant, high impact housing
- Push-to-test switch
- 120 or 277 VAC operation
- Charge rate / power on LED indicator light
- Universal mounting canopy for top or side installation
- NON CEC Compliant
- GREEN LED Exit Sign
- One "EXIT" Faceplate (with optional knockout arrows)
- One Blank Faceplate
- Mounting Canopy, Installation Instructions & Hardware
- NiCad Battery - Must connect the battery after installation
The ELCLEDT-G LED Exit Sign is contructed from injection molded, high impact V-O flame retardant thermoplastic housing. White housing is standard.
Long-Lasting, effecient Green LED's.
Upon failure of the normal utility power, an internal solidstate transfer switch automatically provides uninterrupted emergency operation for at least 90 minutes. The fully automatic solid-state, two-rate charger initiates recharging a discharged battery within 24 hours.
Battery - Battery Backup
The ELCLEDT-G Exit Sign is designed with a maintenance-free 4.8V 900mAh NiCad battery that provides a minimum emergency duration of 90 minutes. Recharge time of the battery is 24 hours. Operational temperature range is 32°F (0°C) to 122°F (50°C).
Dual voltage input 120/277 VAC operation. LED display indicates AC/ON. An external push button test switch allows maintenance personnel to quickly determine the operational status of the unit.
The ELCLEDT-G is suitable for surface wall, top and ceiling mounting via included canopy. Quick connect installation design allows for quick and easy installation. Knock-out chevrons for customized egress signage and field adjustable.View Installation Instructions