Thermoplastic Photoluminescent Exit Signs | 100' Viewing Distance
Base Code: PA3-100
Leading the industry in zero-energy egress systems, these exit signs utilize the latest photoluminescent technology to absorb and store ambient light. In the event of an emergency with blackout or smoky conditions this stored energy is immediately visible, creating a clearly recognizable, photoluminescent egress indicator. These innovative emergency egress signs reduce the risk of panic or injury during an evacuation, offering peace of mind while eliminating energy costs.
This item has been tested and meets safety standards imposed by the Underwriters Laboratories (UL).
This unit uses long lasting, electricity free Photoluminescent Lighting (Glow in the Dark) Technology.
New York City Approved
This product is approved for New York City.
- UL 924 and NFPA 101 Life Safety Code
- Zero energy consumption
- Zero maintenance - no bulbs or battery replacement
- Non-toxic, non-radioactive
- Mounting Options: Wall, Ceiling, and Side
- Consistent, uniform illumination, 100' visibility
- Life Expectancy +25 years
- Operating Temperature 50°F to 104°F
- New York City Approved
- Photoluminescent Exit Sign (Red or Green)
- Mounting Canopy and hardware
- Installation Instructions and Manual
The PA3-100 Series Exit Sign has a thin, low profile construction with ABS thermoplastic paneling and photoluminescent lettering. This wire-free exit sign is high durability, non-toxic, non-radioactive and has a life expectancy of 25+ years.
Provides consistent, uniform illumination at 100 foot viewing distance.
Upon failure of the normal utility power the PA3 exit sign will provide at least 90 minutes of illumination. *The sign must be charged for a minimum of 90 minutes to become fully operational.
Battery - Battery Backup
The PA3-100 Series Exit Sign has a thin, does not require any type of battery connection.
The PA3-100 Series Exit Sign does not require any type of electrical components.
The PA3-100 Series Exit Sign series is suitable for wall mount, ceiling mount, and side mount. Typical ambient lighting is usually sufficient to charge the exit sign. Ambient light levels at sign location should be measured with a light meter to confirm that 5 foot-candles (54 lux) is present on exit sign face(s). There must be a minimum of 5 foot-candle (54 lux) on exit sign face(s) of LED, fluorescent, metal halide or mercury vapor light. *Double Sided Options is not available at this time.