LED Recessed Architectural Emergency Light | Ceiling Mount | Super Bright Large Space Light Spread
Base Code: EL-ARM
Compatible Battery: 6.2V 3200mAh LiFePO4
This item has been tested and meets safety standards imposed by the Underwriters Laboratories (UL).
This unit uses energy efficient and long lasting LED's.
This unit contains a battery for backup power. The battery must be connected during installation.
- UL 924, NEC, OSHA and NFPA 101 Life Safety Code
- Listed for damp location
- LED indicator light with push-to-test switch
- Narrow and Wide Lens
- Universal 120-277 VAC 50/60Hz
- Solid-state switching transistor - eliminates damage contacts
- White Recessed Light
- 2 Lenses (Narrow and Wide)
- Installation Instructions & Hardware
- LiFePO4 Battery - Must connect the battery after installation (Located inside unit)
The EL-ARM Recessed Emergency Light is constructed from 20-gauge steel back box with junction box, trim plate is constructed from polycarbonate plastic. Friendly configuration design for quick and easy installation.
The EL-ARM Recessed Emergency Light use long-lasting, efficient ultra bright white LEDs CCT 5000k. Equipped with 2 types of lenses for different types of illumination needs; wide and narrow lenses.
Upon failure of the normal utility power, an internal solid-state transfer switch automatically provides uninterrupted emergency operation for at least 90 minutes. The fully automatic solid-state, two-rate charger initiates battery charging to recharge a discharged battery in 24 hours.
Battery - Battery Backup
The EL-ARM Recessed Emergency Light is designed with a maintenance-free 6.2V 3200mAh LiFePO4 battery that provides a minimum emergency duration of 90 minutes. Recharge time of the battery is 24 hours.
|Standard Option||50°F to 122°F|
Total Luminaire Lumens : 950lm
Input Wattage: 2.0
Input mA: 25
Standard mounting height of 9ft illuminates 1 footcandle (FC) spaced at 75ft for a 3ft path of egress.
Standard mounting height of 10ft illuminates 1 footcandle (FC) spaced at 80ft for a 3ft path of egress.
Standard mounting height of 12ft illuminates 1 footcandle (FC) spaced at 78ft for a 3ft path of egress.
Spacing is measured in lab condition with an assumed open space, no obstruction and reflection rates of 80 (ceiling) / 50 (walls) / 20 (floor). Actual spacing may vary depending on what environment the fixture is installed in.
Continuously monitors the AC power, battery supply voltage, emergency lamp and charging circuit. The multi-color LED indicator light will indicate failure and adjust when it has been corrected. Unit will automatically perform NFPA required monthly and annual testing. Refer to user manual for details.
Universal voltage input 120-277 VAC 50/60Hz operation. LED display indicates AC/ON. An external push button test switch allows maintenance personnel to quickly determine the operational status of the unit. Features battery over discharge protection.
The EL-ARM is suitable for drop ceiling installations.