LED Recessed Architectural Emergency Light | Ceiling Mount | Aluminum 48' Light Spread
Base Code: EL-LEG
Compatible Battery: 3.6V 3200mAh LiFePO4
This item has been tested and meets safety standards imposed by the Underwriters Laboratories (UL).
This unit uses energy efficient and long lasting LED's.
This unit contains a battery for backup power. The battery must be connected during installation.
- UL 924, NEC, OSHA and NFPA 101 Life Safety Code
- Listed for damp location
- LED indicator light with push-to-test switch
- Narrow and Wide Lens
- Universal 120-277 VAC 50/60Hz
- Solid-state switcing transistor - eliminates damage contacts
- Recessed Light
- 2 Trim Plates
- Installation Instructions & Hardware
- LiFePO4 Battery - Must connect the battery after installation (Located inside unit)
The EL-LEG Recessed Emergency Light is constructed from 20-gauge steel back box with junction box, trim plate is constructed out of aluminum. Friendly configuration design for quick and easy installation.
The EL-LEG Recessed Emergency Light use long-lasting, efficient ultra bright white LEDs CCT 5000k. Equipped with 2 adjustable LED lamps.
Upon failure of the normal utility power, an internal solid-state transfer switch automatically provides uninterrupted emergency operation for at least 90 minutes. The fully automatic solid-state, two-rate charger initiates battery charging to recharge a discharged battery in 24 hours.
Battery - Battery Backup
The EL-LEG Recessed Emergency Light is designed with a maintenance-free 3.6V 1800mAh LiFePO4 battery that provides a minimum emergency duration of 90 minutes. Recharge time of the battery is 24 hours.
|Standard Option||50°F to 104°F|
Total Luminaire Lumens : 400lm
Standard mounting height of 7.5ft illuminates 1 footcandle (FC) spaced at 42ft for a 3ft path of egress.
Standard mounting height of 10ft illuminates 1 footcandle (FC) spaced at 48ft for a 3ft path of egress.
Spacing is measured in lab condition with an assumed open space, no obstruction and reflection rates of 80 (ceiling) / 50 (walls) / 20 (floor). Actual spacing may vary depending on what environment the fixture is installed in.
Continuously monitors the AC power, battery supply voltage, emergency lamp and charging circuit. The multi-color LED indicator light will indicate failure and adjust when it has been corrected. Unit will automatically perform NFPA required monthly and annual testing. Self-testing will take place once a month for 3 minutes and 90 minutes once a year.
Universal voltage input 120/277 VAC 50/60Hz operation. LED display indicates AC/ON. An external push button test switch allows maintenance personnel to quickly determine the operational status of the unit. Features battery over discharge protection.
The EL-LEG is suitable with drywall or drop ceiling mount installations.
Mounting Configurations Explained